Check up to five results to perform an action.
APPLICATIONS: Suitable for exposed and concealed wiring in dry, damp or wet locations, for use in ventilated, non-ventilated and ladder-type cable trays in dry, damp or wet locations, for direct earth burial, also for wiring in all hazardous locations when used with certified HL cable fittings. CONSTRUCTION: Stranded copper conductors, XLP (Cross-Linked Polyethylene) insulated, Method 1 - Table E1 or E2 color-coded or Method 4 phase-identified conductors cabled with suitable fillers as necessary, inner PVC (Polyvinyl Chloride) jacket, aluminum interlocked armor, black PVC jacket overall, surface printed. STANDARDS: * Conductors conform to ASTM B3 & B 8. * Insulation conforms to UL Standard 44, and is approved as Type XHHW-2. * TECK-90/HL Type per CSA Std. C22.2. * Overall jacket approved as Sunlight Resistant and “For CT Use.” * Cables designed to pass the IEEE-383 and IEEE-1202 tests. ** Cables meet requirements of ICEA S-95-658/NEMA WC70.