Check up to five results to perform an action.
APPLICATION: A- Where NEC jurisdiction applies; as 5000 volts shielded power cable, Type MV-105, for use at conductor temperature not exceeding 105 deg.C. in wet or dry locations, when installed in accordance with the National Electrical Code. B- Otherwise, for general purpose applications in wet or dry locations, in circuits not exceeding 5000 volts, phase to phase, at conductor temperatures not exceeding 105 deg.C. for normal, 130 deg.C. for emergency overload, and 250 deg.C.circuit conditions. Suitable for installation in conduit, trays, troughs, ducts, aerial, and direct burial applications. CONSTRUCTION: Stranded copper conductor, semi-conducting layer, EPR insulation, semi-conducting layer, helically applied copper tape shield, three phase-identified conductors cabled together with fillers and a stranded copper ground wire in one interstice, cable tape, PVC jacket overall, surface printed. STANDARDS: * Conforms to AEIC CS8. * Type MV-105 power cable, 5,000 volts. * Overall jacket suitable for Sunlight Resistant and Direct Buried applications. * Sizes 1/0 AWG and larger designed to pass the IEEE-383 flame test and are suitable “For CT Use.” * Cables conform to ICEA S-93-639 and ICEA S-97-682.