Check up to five results to perform an action.
APPLICATIONS: Control or signal cable for important circuits in industrial plants and station control cable for electric utilities where flame resistance is essential. Suitable for the operation and interconnection of protective devices; rated circuit voltage 600 volts; recommended for operation at 90 deg.C. maximum continuous conductor temperature in wet or dry locations. Cables may be installed in open air, in ducts or conduits, in tray or trough, and are suitable for direct burial. Approved for direct burial, Class I, Division 2 industrial hazardous locations per NEC. CONSTRUCTION: Stranded copper conductors, XLP insulated, Method 1 - Table E1 or E2 color coded or Method 4 phase identified, conductors twisted with suitable fillers, PVC jacket overall, surface printed. STANDARDS: * Conductors conform to ASTM B-3 & B-8. * Insulation conforms to UL Standard 44, and is approved as Type XHHW-2. * TC Type Tray Cable per Article 340 of the NEC. * Cables designed to pass the IEEE-383 & IEEE-1202 tests. * Jacket suitable for Sunlight Resistant applications. * Cables meet requirements of ICEA S-73-532 and ICEA S-95-658/NEMA WC70.