Check up to five results to perform an action.
APPLICATIONS: As three- or four-conductor power cables rated 600 volts, 90 deg. C. in dry or wet locations. Specifically approved for installation in cable trays per Article 340 of the NEC. Type TC cables are permitted for use in Class I Division 2 industrial hazardous locations per NEC. Cables may be installed in free air, raceways or direct burial, in wet or dry locations. All cables when used in accordance with the NEC, meet the requirements of OSHA. CONSTRUCTION: Stranded copper conductors, XLP (Cross-Linked Polyethylene) insulated, Method 1 - Table E1 or E2 color-coded, or Method 4 phase-identified. Insulated conductors cabled with a stranded copper grounding conductor in one interstice, cable tape, CPE (Chlorinated Polyethylene) jacket, surface printed. STANDARDS: * Conductors conform to ASTM B-3 & B-8. * Individual conductors conform to UL Standard 44, and are approved as Type XHHW-2. * TC Type Tray Cable per Article 340 of the NEC. * Cables suitable for Sunlight Resistant applications. * Cables designed to pass the IEEE-383 & IEEE-1202 flame tests. * Cables meet requirements of ICEA S-95-658/NEMA WC70.